Question-and-Answer Resource for the Building Energy Modeling Community
Get started with the Help page
 Ask Your Question

# a burst of humidity in Energyplus

Hi, I would like to input [gH2O/h] in Energyplus simulation to take into account burst of humidity within 9 hours. Thank you.

edit retag close merge delete

## Comments

What causes this burst of humidity? Is it a water draw like a shower or sink connected to a domestic hot water system or something similar? Is it something inside of a zone that uses electricity or gas? More information would be helpful.

( 2020-07-24 14:22:36 -0500 )edit

i want to validate an experimental results; it just a an increase of humidity in the zone!!!

( 2020-07-25 04:38:43 -0500 )edit

## 2 Answers

Sort by ยป oldest newest most voted

First off, you have many options to define latent moisture gain entering a zone in EnergyPlus. If some electricity consumption causes this latent moisture gain, then you should use the ElectricEquipment object in your input file. There are other objects to use if latent moisture gain is caused by using gas, or as @rraustad pointed out in their answer the OtherEquipment object that will add moisture without consuming any energy.

No matter what option you use to define the latent moisture gain, you cannot directly define moisture addition to a zone in terms of water mass rate like $g_{water}/hr$. You will instead need to define multiple inputs that will together set this water mass rate gain:

• Energy use of the equipment (total design level in $W$, power per area in $\frac{W}{m^2}$, or power per person in $\frac{W}{person}$ )
• Fraction of the equipment's energy use that becomes latent gain. As @rraustad says, this should be set to 1 so that all of the energy use becomes latent gain to the zone.

The basic calculation for the "power" of latent gain into a zone is:

$$Power_{latent} = \dot{m}_{water}*h_{fg}$$

Where $h_{fg}$ is the heat of vaporization of water (2256 $\frac{kJ}{kg}$ at 100 $^oC$). So, you should multiply your desired $g_{water}/hr$ by $h_{fg}$ to calculate the equivalent $W$ of latent gain to enter as an EnergyPlus input for Design Level.

more

## Comments

thank you so much this is so hopeful @Aaron Boranian

( 2020-07-25 11:32:18 -0500 )edit

You could use the OtherEquipment object with a Latent Fraction = 1 to add moisture to a zone based on a schedule.

OtherEquipment,
MoistureInjector,        !- Name
None,                    !- Fuel Type
ZONE ONE,                !- Zone or ZoneList Name
MySchedule,              !- Schedule Name
EquipmentLevel,          !- Design Level Calculation Method
352,                     !- Design Level {W}
,                        !- Power per Zone Floor Area {W/m2}
,                        !- Power per Person {W/person}
1,                       !- Fraction Latent
0,                       !- Fraction Radiant
0;                       !- Fraction Lost

more

## Comments

thank you sir but i didn't find any column to put 500g/h how can convert g/h to watt?

( 2020-07-25 04:47:57 -0500 )edit

and what is the mean of design level

( 2020-07-25 05:21:23 -0500 )edit

Design level is the max output and this value is multiplied by the schedule. So if your schedule is all 0 except for a time period of your choosing then the moisture generator will be off most of the time.

( 2020-07-27 07:49:19 -0500 )edit

You could configure the schedule object to consider the "burst of humidity" in 9 hrs.

( 2021-06-28 14:28:39 -0500 )edit

## Your Answer

Please start posting anonymously - your entry will be published after you log in or create a new account.

Add Answer

## Stats

Asked: 2020-07-24 12:15:41 -0500

Seen: 486 times

Last updated: Jun 25 '21