Question-and-Answer Resource for the Building Energy Modeling Community
Get started with the Help page

# Adjust U-Value of 4 layer ETFE Cushion

Hi all,

I´m working on a project with an ETFE envelope, both for the facades and roof. These are made of 4-layered cushions with air gaps between them. To model the cushions in E+ I´ve used the detailed specs from the manufacturer as WindowMaterial:Glazing WindowMaterial:Gas objects.

E+ outputs show a resulting U-Value of 1.28 W/m2K which according to the local technical standards needs to be increased by 0.5 W/m2K to account for the curved nature of the cushion (and varying air gap thickness). Essentially a "safety factor".

Is there a way of doing so?

I´m aware of the WindowMaterial:SimpleGlazingSystem object, but that would change the thermal interaction between the ETFE layers, and affect the resulting internal cushion temperature - which is key for the comfort on the last floor, right below the roof.

It seems quite tricky to account for this safety factor while maintaining the precision that WindowMaterial:Glazing brings in this particular case. Has someone faced something similar?

edit retag close merge delete

Sort by » oldest newest most voted

If there is someone following the topic, the solution ended up being relatively easy.

I just adjusted the thickness of the air gaps between the ETFE films until I got the corrected U-value. The resulting U value can be checked in two ways, either in Window7.7, where I had first assembled my construction or in E+ (this last option requires running the model and checking the output files). I found the iterative testing faster in Window7.7, then followed by a final check on E+ output to confirm the value.

more