Question-and-Answer Resource for the Building Energy Modeling Community
Get s tarted with the Help page
 Ask Your Question

Ground Slab/basement Modelling-water reservoirs and wells

Hi, I am using Eplus 8.9.

i was wondering, which considerations should I have to do if I have a water reservoir under the slab that acts as a buffer with the soil temperature?

Best

edit retag close merge delete

1 Answer

Sort by » oldest newest most voted

If the water reservoir is at known temperatures, you could use this directly as the slab outside boundary condition, using OtherSideCoefficients as the outside boundary condition (see SurfaceProperty:OtherSideCoefficients) to set scheduled outside surface temperatures.

Or, if the reservoir is stagnant, I suppose you could added it as another layer in the slab construction.

more

Comments

Sorry for replying so late.

Basically I have a rainwater cistern made up of waterproofed boundary walls and slab, below the conditioned zone. The water level varies over the year so if we look as a section we will have (top to bottom): slab, air layer, water, slab, ground.

do you think that considering half air layer and half water (in term of thickness) is a correct assumption, don't you?

( 2018-12-25 13:39:11 -0600 )edit

That's a starting point, but the cistern has side walls which add another dimension to the heat transfer, and possibly more important is the effect of rain water entering the cistern.

( 2018-12-26 14:48:52 -0600 )edit

So if I am not mistaken I need to assess in such a way the 3d through the entire assembly and then add it into eplus as an equivalent construction? Do you think I would need a finite element analysis in order to model the ground slab?

Finally What about the thermal mass of the entire equivalent assembly? in this case is not appropriate to use a R-value material, to my knowledge. What do you think?

thanks in advance

( 2018-12-27 05:22:18 -0600 )edit

Given that the thermal mass varies as water enters and leave the cistern, and these flows move energy in and out of the cistern, it's not clear that an equivalent assembly will come anywhere close to representing the dynamics of the cistern. Even a simple spreadsheet model of the cistern would be better than trying to mash it into an equivalent 1-d surface. With a model of the cistern outside EnergyPlus, you could produce a schedule of surface temperatures to apply using OtherSideCoefficients.

( 2018-12-31 08:17:51 -0600 )edit

Your Answer

Please start posting anonymously - your entry will be published after you log in or create a new account.

Add Answer

Stats

Asked: 2018-11-19 06:27:19 -0600

Seen: 124 times

Last updated: Dec 04 '18