Problems with modelling Radiant cooling and VRV in Design Builder
Greetings. I am Kartikay Sharma (firstname.lastname@example.org), student for MTech Building Energy Performance at CEPT University. I am Right now using Simulations as a tool in my thesis to estimate the energy savings potential of buildings. For this purpose, I am using DesignBuilder to simulate all ECM/EEMs. Three of my selected ECMs are : 1. ECBC compliant chiller(centrifugal with 6.3 COP with VAV AHU and VAV terminal units) 2. VRV systems 3. Radiant cooling
My base-case system uses a water cooled system with an screw chiller of 5.2 COP and Constant Air Volume (CAV) AHU. The problem that I am facing is that, I am getting higher savings(overall EPI savings) if do ECM1 listed in table, but looking at case studies the savings from ECM3 should be higher than ECM1. Similarly I am facing problems with ECM2. The weather selected for my building is Hot and Dry climate of Ahmedabad.
So I request all the members to help me in the same